Welcome to our site! EDAboard.com is an international Electronics Discussion Forum focused on EDA software, circuits, schematics, books, theory, papers, asic, pld, 8051, DSP, Network, RF, Analog Design, PCB, Service Manuals... and a whole lot more! To participate you need to register. Registration is free. Click here to register now.
You have to check the max/min loads for your equipment which sources the 4-20mA signal.
I read this type of signals from Infrared flame detectors or IR-gasdetectors which can source up to 500 Ohms max.
A new feature in this are HART devices which uses the same wires for a 485 like data transmission to a handheld interrogator.
If you like to use this protocol then the load resistor should not be less then 250 Ohms.
I really don't think a load resistor of 1 Ohm is desired for industrial type of equipment.
First of all: what equipment do you have?
Datasheets? Describe your application a bit more. We really like to help, but we only can help if you provide us with good description of what you need.
Generally spoken the load resistors for 0-20mA devices are around 200-500 Ohms.
If you like to read the value with an analogue input of a PIC then Use a 200 Ohms 1% resistor for load. Normally spoken these devices have an overrange and max source of 25mA. In this setup you can read 0-5V at the input of the PIC. Use some protection circuit if interfacing field wiring.